|Rated operating voltage ||220VAC50HZ |
|Rated operating current ||1A-63A adjustable (default 40A) |
|Undervoltage action cut-off value ||210V-145V(default 170V) |
|Overvoltage action cut off value ||230V-300V (default 270V) |
|Limit current Protection ||Depends on Rated current |
|Power delay after power off ||30s |
|Own power consumption ||2W |
|Electrical machinery life ||More than 100,000 times |
|Dimensions ||81*35*60mm |
|Working temperature range ||-5 ~ 45C |
|Relative humidity ||45 ~ 90% RH 40C |
|Altitude ||Less than 2000m |
|Degree of protection ||IP 20 |
|Mechanical durability ||1000000 cycles |
|Dielectric strength ||>2kVAC 1min |
|Weight ||200g |
|Dimensions (H x W x D) ||80X43X54mm |
|Mounting ||35mm DIN rail |
Mainly used for home and similar use of low-voltage distribution lines, when the line over voltage or undervoltage failure can automatically disconnect, and can automatically detect the line voltage, when the line back to normal when the automatic closure.
Products with high-speed low-power processing as the core control, high load capacity magnetic holding relay for the main control circuit, with online production voltage LED digital display, indicator light status indication, the product can be sustained under high pressure shock.
Timely protection of the safe use of load appliances. Product protection action when the neutral line is not open, in the installation should be consistent with GB16895.21 and other relevant installation procedures.
1.Press and hold the “SET” button for 3 seconds to enter the
parameter setting state.
1.1 When "Over(V) LED On,It means Setting the Over voltage
Value state,Press "UP" and "Down" can adjust the Over Voltage
value. default value is 270V
1.2 Press "SET" When "Under(V) LED on,It means Setting the
Under Voltage value state,Press "UP" and "Down" can adjust the
Over Voltage value. default value is 170V
1.3 Press "SET" When "Current (A) LED on,It means Setting the
Limit current value state,Press "UP" and "Down" can adjust the
Limit cureent value. Default Value is 40A.
2.When All data are set already,wait 40sec,then connect the
3. Press "UP" and "Dwon",reset the to default value.